Flat level surface for container installation
It is possible to place the container in the open
Ambient temperature;from -35 ° C to +35°C
Ventilated platform;15 х 5 м.
Minimum floor-to-ceiling height;5 м.
Electricity supply;3 phase 380V
Ventilation, consumption;15 kW
Aggregate consumption;600 кВт
It is necessary to connect two power cables AVVG 4х240 from the transformer.
Cooling in the container is organized in the freecooling way. Air gets into the container through a filtering chamber and then comes out through devices cooling them by that.
32 filter class G3 comes with the container.
Filters are removable and easy to service (they can be washed as they become dirty).
The air mixing system of the cold and hot zones has been implemented for the cold season.
Any client's additions as agreed
Smoke detection sensor
Installation of Management Software
Netping automatics allows to conduct remote control and receive notifications about the following parameters: temperature inside the data center, loss of voltage on racks, movement inside the data center, opening / closing of doors, humidity level
1-2 containers;1,750,000 ₽
more than 2 containers;1,550,000 ₽ (discount 12%)
Production of Containers;Irkutsk region